Sioux City, Iowa
The school’s maintenance staff noticed the boiler was leaking, but were unable to determine where it was coming from, and why it was happening. They contacted us for help. Upon inspection, we found that the turnaround area was rotting out. Rasmussen removed the rear tube sheet and replaced it with a new tube sheet and stay bolts. The boiler was hydrostatically tested and approved by an authorized inspector.
- 0 incidents
- Performed Code compliant repair on a boiler from the 1950s
- The repair met all NBIC and ASME requirements